The development of highly efficient and environmentally friendly burner system fired utility power
1. State registration number: №0113U000997, NTUU "KPI" 2639-P.
2. Scientific adviser - prof. Varlamov Gennadiiy B.
3. The essence of development, the main results.
For steam and hot water boilers installed burners known requirements to systems, namely, versatility, reliability, stability and stabilization ignition combustion front widely, given intensity mixing software, ensuring the completeness of combustion gas with minimal excess air ratio, maintainability, high energy environmental efficiency, minor upgrades and payback period. These requirements were the basis for drafting the burner system for municipal energy boilers. For performance was analyzed major communal energy Kyiv region and selected for research boiler PTVM-180 st№2 branch "CHR-5" PAT "KYIVENERGO."
To ensure high performance and environmentally safe operation of the burner as a basis during its creation was elected tubular technology gas burning (TGB), which is based on the rational use of aerodynamic effects of flow in the nozzle Bordeaux is the basic building block. The choice of nozzle Borda as a basic element of the new technology of combustion of hydrocarbon fuels due to the fact that hydraulic and aerodynamic characteristics of the element facilitate implementation of the "canonical" principles of minimizing toxicity burners (pre-mixing, phasic combustion ramjet aerodynamic scheme). The intensification of the process of mixing and stabilization of the combustion process is due to the existence of a ring circulation flow (vortex stabilizer) that occurs in the nozzle Borda.
Tubular modules as stabilizers and angular pylons, forming the so-called regular fuel burning system, giving universal design burners. However, the use of tubular modules compared to the flat there is an additional stabilizers "linking" effect that promotes intensification of heat-mass transfer processes.
TGB peculiarity is that when single-threaded air supply and fuel supply of multi realized "enshrouding" effect gas jets central air jet. As a result of intensive mixing in the boundary layer air stream there tugging local diffusion torches, forming almost uniform integrated system torches.
In multimodal performance burners is no need to install external modules in each nozzle, as in this case, there is a natural area of interface between adjacent modules that performs all the functions of positive external nozzle.
One of the special properties of flare systems based on tubular modules is their structural simplicity and technology combined with a variety of methods including mixing, diffusion, and the previous combined.